A few times a year I get asked to gas pipe in a generator, in this case it was to a Kolher 30kw.
Because a 30kw generator takes more gas than what a normal household gas line can carry the customer had the gas company install a high pressure gas meter. We then installed a pressure regulator at the generator location. This way we had plenty of fuel for the larger generator.
Above you see the new gas line with a new regulator installed. You will also notice we added a pressure gauge and bleeder after the regulator. My customer wanted to be able to monitor the pressure and bleed of any air or gas if need be.
Heating And Cooling Skagit County
Need a Heat Pump, Air Conditioner, Furnace, Boiler or Tankless Water Heater? We install them all over Skagit county including Mount Vernon WA, Burlington WA, Anacortes, Sedro Woolley, La Conner, Stanwood WA, and on Camano Is.