Trane AC R22 Replacements.
Both these Trane Air Conditioners have damaged compressors. Both units where shorted to ground and one of the two units was even completely dry of refrigerant.
Fortunately for my customer you can still purchase R22 air conditioners, but the units must come dry with no refrigerant in them, otherwise they would have had to either just replace the compressors or completely replace both the indoor and outdoor equipment with R410a equipment. This would have been a very costly way to go for my customer.
The new American Standard R22 units above came with no refrigerant but charged with nitrogen instead. We simply had to recover the refrigerant out of one of the existing units, set the new units, braze in, and then pressure test the entire system with nitrogen. Once the test was over we pumped down both systems below 500 microns then charged with R22. We did add filter driers as well as sight glasses to complete the project.
Heating And Cooling Skagit County
Need a Heat Pump, Air Conditioner, Furnace, Boiler or Tankless Water Heater? We install them all over Skagit county including Mount Vernon WA, Burlington WA, Anacortes, Sedro Woolley, La Conner, Stanwood WA, and on Camano Is.